Try our new smart phone app and find the perfect conduit for your requirements!
Non-metallic conduits and FLP up to 34mm can be easily cut with Flexicon Conduit Cutters, part no. CC01. Use CC02 for sizes up to 67mm. Drop the blade into a corrugation and squeeze and twist until conduit is cut 50% through. Cut the remaining 50% without twisting to achieve a square cut.
Metallic conduits should be cut with a fine tooth (32 TPI) hacksaw or bandsaw. Ensure you make a straight vertical cut. Our clamping vice, part no. BSB makes the use of a hacksaw much easier.
Cutting of overbraided conduit is made much easier by tightly wrapping self adhesive tape around the conduit and sawing through the middle of the tape. The tape should be removed if EMC screening is required. Ensure you make a straight vertical cut.
Flexicon offer a bench mounted bandsaw designed to cut metallic conduit easily. Conduit length is measured under light tension. When cutting an exact number of lengths from a reel (e.g. 5 x 5m from 25m) please take into account the length tolerance of the reel and each cut length.
Our range of non-metallic conduit fittings, Flexilok®, FPA and FPAX are all push fit fittings which are quick to assemble once you have cut the conduit to length.
For Flexilok® and FPA fittings simply push the conduit into the end of the fitting with a slight twist until it will go no further. Pull back slightly to ensure the locking teeth mechanism has engaged with the corrugations
The FPAX fitting features a conduit seal to provide the ultimate IP rating up to IP69K. This simply fits onto the end of the conduit before the fitting is connected to the conduit. To aid assembly moisten this seal. An FPA fitting cannot be uprated to IP69K with the addition of a seal. Pull back slightly to ensure the locking teeth mechanism has engaged with the corrugations.
To remove the FPA or FPAX fittings simply insert a small screwdriver into the screwdriver slot and move the screwdriver handle towards the "off" position. Remove the screwdriver then manually twist the cap further towards the off position - the fitting can then be released from the conduit. Once removed, the fitting can be reused by simply twisting the cap so that the screwdriver slot lines up with the ON position.
Our fitting\'s components are supplied part assembled to illustrate how they go together. Our C type fittings consist of a compression nut, an elastomeric seal, an insert and a body.
Firstly place the back nut on the conduit followed by the seal (note the orientation). Next, screw the insert into the end of the conduit until this gives a secure fit.
Bring the body to mate with the back nut. Metal fittings should be tightened with grips or spanner to ensure security and IP rating..
To obtain EMC screening on pliable FLP conduit, the PVC sheath must be trimmed back prior to assembly of the fitting to ensure good electrical contact with the tapered bore of the fitting body as shown
Snap in Flexilok® fittings can be removed by using a tool
If you are unsure of any of the requirements below leave the box blank.Please submit the form below
Sign up for further details...